Ballast Factor Affects Light Output
Ballast factor is a number normally between 0.70 and 1.2. This number is a multiplier applied to the rated initial lumens of a light bulb. The result tells you how many lumens are actually delivered from the bulb/ballast system. In some cases the result will be fewer lumens than the lumen rating for the bulb alone (Low Ballast Factor). In other cases, the result will be roughly the same lumens as the bulb alone (Normal Ballast Factor), or more lumens than the bulb alone (High Ballast Factor).
To add to the confusion, a ballast can have different ballast factors depending on the type of light bulb connected to the ballast. Example: a 32 watt T8 bulb may have a ballast factor of 0.89 and a 17 watt T8 bulb connected to the same ballast may have a 1.06 ballast factor.
Ballast factor tells you how much light (lumens) you will get from a specific bulb/ballast combination. Because low ballast factor ballasts use less power than normal or high ballast factor ballasts, they may be used where lower energy costs are the goal of a lighting retrofit. In new construction, high ballast factor ballasts may be used because the higher bulb/ballast light output will allow fewer fixtures to be installed, for example, in a large open office.
Power Factor Affects the Electric Utility
Ballast Power Factor measures how “efficiently” a ballast uses its power. Expressed as a percentage, 0% to 100%, power factor is the ratio of power used by a ballast compared to the total power supplied by the utility: Power Factor = Watts/Volt-Amperes. In most cases the power factor is less important to the owner of the ballasts than to the electric utility. Low power factors cause the current delivered by the utility to the building owner to be out of phase with the voltage. When this happens, the utility has to supply more volt-amperes. Large commercial or industrial customers may be charged an additional fee if their power factor is too low.
Shop Fluorescent Ballasts Now
Latest posts by Dave Burtner (see all)
- Connected Control: Know Your Options for Commercial Outdoor Fixtures - October 2, 2018
- MR16 Luminous Intensity: How Does LED Stack Up Against Halogen? - September 20, 2018
- Lighting Reference: New Smart Phone & Tablet App from the IESNA - September 6, 2018
- LED Fixture Efficacy vs Quality of Light: Recent Study Provides Insights - August 23, 2018
- Compare Your LED Upgrade Options: A Simple Decision Guide - August 13, 2018