If you choose T8 LED tubes with an internal driver as a replacement option for T8 fluorescent retrofits, you must be aware of an important issue relating to sockets.
Generally, an electrician completes this type of retrofit because of the re-wiring requirements. A critical step to be followed in the installation involves inspection of the existing G13 sockets (lampholders) to determine how the contacts in the socket function.
Shunted vs. Non-Shunted Lamp Sockets
The contacts in shunted sockets connect directly at the socket so power moves from one contact to the other. It’s important to note that the “shunt” may be internal to the socket and invisible.
To confirm which type of socket is in the existing fluorescent fixture, a voltage meter should be set to “continuity”. If the two socket contacts show positive continuity, power flows between the contacts and the socket is shunted. These sockets must be replaced with non-shunted type for the LED retrofit to operate properly. If there is no continuity across the contacts, the sockets are non-shunted and can be used with the LED tubes.
Why is this important? For LED tubes with internal drivers, the retrofit involves removing the existing ballast and rewiring the fixture so 120V or 277V power connects directly to the socket.
If the socket is shunted, a dead short will blacken the socket and cause damage to the LED tube.
Shop LED T8 Bulbs
Latest posts by Dave Burtner (see all)
- LED Direct Replacement: A Guide for 26W, 32W and 42W 4-Pin CFLs - October 25, 2018
- Step-by-Step Guide: LED Troffer Replacement - October 16, 2018
- Connected Control: Know Your Options for Commercial Outdoor Fixtures - October 2, 2018
- MR16 Luminous Intensity: How Does LED Stack Up Against Halogen? - September 20, 2018
- Lighting Reference: New Smart Phone & Tablet App from the IESNA - September 6, 2018