The specifications for light fixtures often include a value for IP, the abbreviation for International Protection Marking (sometimes referred to as Ingress Protection Marking). The IP rating system is an International Electrotechnical Commission (IEC) standard that applies to many product categories including lighting.
Why IP Ratings Are Important
The IP rating informs the buyer how well protected the light fixture is against particulates and water getting inside the fixture to cause damage.
Fixtures intended for outdoor installation and shower rooms are two obvious examples of applications where it is important to know how well sealed the fixture is against moisture and water penetration.
Other examples include fixtures located in food processing plants where they will likely be exposed to direct contact, high pressure water during hose-down at the end of a shift.
Similarly, fixtures located in warehouses and industrial applications can be subjected to very dusty, high particulate environments that, if not well protected, could cause poor illumination performance or even damage to the fixture.
Each of these examples will require fixtures with a different level of particulate and water protection. The IP rating provides the necessary information.
Decoding the IP Rating
The IP metric is a two digit numerical value.
The first digit denotes the level of protection against solids – particulates, dust and other solid objects in the environment. Higher numbers mean the fixture enclosure gasketing is designed to prevent the entry of smaller and smaller particulates.
The second digit refers to the level of protection against liquids. Low numbers mean limited protection, higher numbers mean greater protection with the highest number, 8, meaning the fixture is sealed well enough to be completely submerged in water without damage.
The IEC publishes two tables explaining precisely the protection level referenced by each digit in the IP rating. Below is a summary version of these tables.
IP Rating: First Digit (Protection against solids)
- 0 – No protection against entrance by an object
- 1 – >50 mm in size; fixture protected against entry
- 2 – >12.5 mm in size; fixture protected against entry
- 3 – > 2.5 mm in size; fixture protected against entry
- 4 – >1 mm in size; fixture protected against entry
- 5 – Dust protected; dust has to enter in large amounts to interfere with operation
- 6 – Dust tight; impossible for dust to enter
- x – Undetermined; not defined
IP Rating: Second Digit (Protection against liquids)
- 0 – No fixture protection against entry by water
- 1 – Dripping water; no damaging effect on fixture against vertical dripping water
- 2 – Dripping water tilted up to 15°; no damaging effect on fixture against vertical dripping water
- 3 – Spraying water; no damaging effect on fixture at any angle up to 60°
- 4 – Splashing water; no damaging effect on fixture at any angle
- 5 – Water jets; no damaging effect on fixture from water projected by a 6.3 mm nozzle
- 6 – Powerful water jets; no damaging effect on fixture from water projected by a 12.5 mm nozzle
- 7 – Immersion up to 1 m; water will not enter the fixture
- 8 – Immersion beyond 1 m; fixture is suitable for continuous immersion in water
Examples: Two Fixtures with IP Rating
Porch Light with IP44. This fixture has moderate protection particulates and is protected against splashing water. This modest level of ingress protection requires a sheltered outdoor installation.
Wall Pack with IP65. This fixture has 100% protection against entry of dust or particulates and it is protected against damage from water jets. This high level of protection against both dust and water means this fixture can be safely installed where it is fully exposed to environmental dust and all rain conditions.
Not all fixtures will have an IP rating. But, especially for outdoor fixtures, the rating is a valuable metric when evaluating how well a fixture will perform in the location where it will be installed.
Shop IP Rated Fixtures
Latest posts by Dave Burtner (see all)
- Planned Maintenance Integral to the Long Term Benefits of LED Lighting Systems - April 18, 2018
- Lighting Uniformity: Study Shows An Important Advantage of LED Fixtures for Parking Lots - April 5, 2018
- Evaluating an LED Retrofit of HID High Bay Fixtures in a Maintenance Facility - March 26, 2018
- How to Make Sure Photocontrols Are Compatible With LED Lighting - March 14, 2018
- A Guide to Beam Metrics for Comparing LED to Halogen Directional Lamps - March 1, 2018